The system is divided into inner circulation and outer circulation. The inner circulation medium is cooling liquid, and the outer circulation medium is tap water; the system is equipped with a filter to filter the inner and outer circulation. The filter needs to be cleaned after the system runs for a while.
The filter is divided into three parts, and the corresponding cleaning time requirements are as follows:
1) The cooling tower spray pump suction mouth filter, the cleaning cycle is once a month;
2) The Y-type filter is circulated in the liquid supply system of the pump group, and the cleaning cycle is once a year;
3) The Y-type filter is circulated in the rehydration system of the pump group, and the cleaning cycle is once a year;
The cleaning method is: washed with water, rinsed, and dried before use.
*Note: This is the water-cooled container parameter of the AVIC 1.3 version. If your product is from other manufacturers or versions, it may differ slightly from this parameter. This parameter is for reference only.